Benton IL Air Conditioning and Heating Services
Charlie’s Air Conditioning & Heating has provided Benton, IL with excellent service for over 30 years. We specialize in heating and air conditioning products and services, as well as insulation upgrades.
Read our excellent reviews and find out why your Southern Illinois neighbors consider us to be their nearby heating and air company in Benton, IL.
for Benton, IL
Our Reviews by City
He did a great job, very polite.
Juanita - Benton, IL
I really appreciated his honesty.
All around excellent
Potts - Benton, IL
This company is always puts the customer first. Technicians are very knowledgeable, proficient while maintaining excellent customer relations.
Quote for 3 ton air conditioner and 95% gas furnace
Gas smell when furnace running. Weâ€™re here 2 weeks ago. Bubbles and used leak sniffer on every fitting, system on and system off. Found no leaks. Checked co, sniffed for gas throughout house, no hits. Told them if they smell it again to call us or their utility
Inducer wines a little, amps fine and runs very cool. All checks good. Starting pcsa
No heat inducer going bad, oiled bearings, itâ€™s running. Ordered new part, will return tomorrow to replace Replaced inducer
PCSA PREPAID 2020 Heating Equipment Maintenance Maintenance on main house heat pump. Tested electric heat, inspected all electrical, checked filters. Tested heat pump, tested defrost, checked charge system is heating Checked unit above garage, Valerie said it was going to emergency heat. Found system out of gas, open compressor winding and bad outdoor capacitor. Last summer we added 5 lbs clean r22 at no charge to get through the summer. Added 2 lbs clean r22, could not get winding to close. Set system to emergency heat Spoke to Valerie, would like to talk to Pete Call her at the office 937-1411
Thermostat doing the same error as last time. NO HEAT Error code 44 and 41. Troubleshot system according to carrier manual, found the blower control module bad, also got bad winding readings. Quoted $1794 for new motor and module Original installer said they will cover it
2020 Fall pcsa communication error from thermostat, found condensate safety tripped. Cleaned pump, flushed water. Checked heat pump everything going good, replaced filter
Southwest system left twin is operating normally. Right twin is dead. Southeast system left twin is dead. Right twin is operating normally. Reattached return air flex. Northwest left twin needed new blower capacitor and outdoor capacitor. Right twin is dead (new compressor and blower motor.) Northeast system left twin needed new outdoor capacitor. Right twin needed new blower capacitor and thermostat wire repair.
No AC blown capacitor, replaced added 1# R-22
Replaced evaporator coil
Came home to a house full of haze, coil has popped a leak indoors. Pumped down unit, got key to come back tomorrow replace coil, gases up her upstairs garage unit so she could sleep up there tonight 7/10...replaced coil, fixed leaks in liquid line, pressure tested to 150 psi, evacuated to 500 microns, added 9 lbs 410a. Redid drain line, was leaking, 18 degree temp split system is cooling