Air Conditioning and Heating Experts in Sesser IL
Charlie's Air Conditioning & Heating has provided Sesser, IL excellent heating and AC service, repair, installation, and system replacement for almost 40 years. We specialize in heating and cooling services as well as blown-in insulation.
What Makes Charlie's Different (and Better!) for local Sesser families?
Why pick Charlie's Air Conditioning & Heating as your HVAC contractor? We have been trusted to heat and cool local homes and have the expertise to keep you cool and comfortable in the summer and nice and warm in the winter. We also stock a variety of American-made products that could change how you interact with your heating or cooling system.
We install only YORK products so we can provide you with the finest examples of furnaces, air conditioners and heat pumps. Upgrading and get significant savings on your utility bills as the new HVAC systems are built to operate at maximum efficiency.
Check out our glowing reviews and discover why your neighbors consider us to be their nearby heating and air company in Sesser, IL.
for Sesser, IL
Our Reviews by City
Wilhelm - Sesser, IL 62884
Thank you for the expertise and professionalism.
Tim - Sesser, IL 62884
Quote for 3 ton 15.2 SEER2 heat pump install
AC Maintenance PCSA 2023 AC Check Up Prepaid Completed cooling maintenance, cleaned coils, flushed drain, filter is provided by customer, checked air temps, checked compressor and condenser fan amps, checked capacitor, made sure system is working properly System is cooling at this time
Complaint: No AC - No air blowing through vents. System was not running due to 24v wire being hit and split by weed-eater. Repaired wires and verified operation of system. It is cooling at this time.
Complaint No AC. System was low on refrigerant again, added 4lbs and verified it had a good temp drop and proper sub cool. There is definitely a leak in the system, bubbled a few joints and couldn’t find one. We need to get back out here ASAP and perform a thorough leak search.
AC Repair Complaint: No AC Found unit cycling on low pressure switch, added 3 lbs 410a. Unit holds 8 lbs so it’s apparent there is a leak. Looked over unit, no signs of leaks, checked service valves, no leaks. Would recommend coming back and doing a leak search. In the meantime, system is cooling
Quote for AC repair vs. Air Conditioner replacement
PCSA 2022 Heating Check Up Renewal<br> All checks are good. Filter is clean and changed monthly.
Pulled and cleaned coil. Fixed drain and put in a filter
Complaint no heat Only way this coil can be cleaned is if the coil is pulled and taken outside to be washed off. Neither cooling nor heating will function properly with this issue. Shooting for tomorrow on schedule. Tenant has been informed and says she will leave door unlocked
Complaint water issue Drain not clogged. Pan was clogged. The inside edge of the drain pan under the evap coil has a very small channel for water to run through. It was slimed up. I flushed it all out and put some drain tablets in. No drip at this time. I also replaced her filter upon request. It was due.
PCSA 2022 PREPAID AC CHECK UP All checks good, made new screw holes for blower door, filter changed by customer
Sealed shield with silicone, replaced both capacitors, ran a mini drain to keep water off the curb. All checks good, 26 degree rise
No cool ductwork is rotted under house, needs box fixed, 2 sections of trunk, radius elbow and remove all work. Told customer weâ€™re 2 months out, they would like it scheduled