De Soto IL AC and Heating Experts
Charlie’s Air Conditioning & Heating has delivered De Soto, IL excellent service for almost 40 years. We specialize in heating and air conditioning services as well as blown-in insulation.
Check out our glowing reviews and discover why your neighbors consider us to be their nearby heating and air company in De Soto, IL.
for De Soto, IL
Our Reviews by City
Autry - De Soto, IL
Chipc73 - De Soto, IL
Daniel did an excellent job checking our system. Charlie's has always been a first-rate company with which to do business. Highly recommended.
Ashtyn - De Soto, IL
2021 2 system a/c check up free
Complaint: No Heat / Carrier unit about 25 years old throwing code of 33. Has had moisture issues in the past. Rotten roll out swt. Bad hose will order ASAP. Replaced parts. Replace roll out swt. & hose kit.
2021 PCSA AC Check Up Renewal Replaced single run capacitor inside for blower All other checks good Drain flushed Disconnect requires immense strength
PCSA 2021 AC Check Up Renewal
Replaced contactor under parts warranty Declined filter change
Heat not keeping up Told mike and his wife to monitor light if it comes on agin let us know if it throws a code, all electrical working and no fault code and refrigerant charge accurate at this time
PCSA 2020 Heating Maintenance
Ckd. System unit in good order no issues found . T-stat canâ€™t adjust time.
Customer needs billed husband has checkbook for different account for this house
Customer changes filters regularly, all checks good, does not have an email
2020 Heating Check Up Renew & Scheduled 11/10/20 2021 AC Check Up Included Customer changes filters regularly, all checks good
2020 Heating Check Up Prepaid
Everything was clean and checked out well.
PCSA 2020 Heating Equipment Maintenance RENEWAL PCSA 2021 Cooling Equipment Maintenance Included Showed customer pitted contactor suggested replacement
PCSA Spring 2020 Cooling Check Up Renewal Fall 2020 Heating Check Up Included Valve core on suction line was leaking. Replaced core and added 1 lb of R-410A. Everything else was clean and checked out well.
Complaint: No AC No ac found bad capacitor, replaced capacitor, checked charge system is cooling
During the spring 2020 check up that was done on July 2, 2020 Steve found a weak 60/3 capacitor it was below the manufacturer specifications. Need to order capacitor. Ordered and returned and replaced.