Herrin Calls Charlie’s for HVAC Issues
Charlie's is Your Local, Trusted Heating and Air Conditioning Provider
Serving Herrin and Southern Illinois Since 1982
Herrin residents know who has their back when it comes to staying warm in the winter and cool in the summer. Charlie's Air Conditioning & Heating has been in business for over 30 years, providing reliable products and trusted service. We combine old school values with cutting edge technology to ensure our clients in Herrin and throughout Southern Illinois are always 100% satisfied.
What Sets Charlie's Apart in Herrin
So what is it about Charlie's that could make you dump your old HVAC company? Like most HVAC companies, we can keep you cool and comfortable in the summer and nice and warm in the winter. But did you know we also stock a variety of American-made products that could change how you interact with your heating or cooling system?
We install only YORK products so we can provide you with the finest examples of furnaces, air conditioners and heat pumps. Upgrading these appliances can mean significant savings on your utility bills as units are now built to operate at maximum efficiency.
Call Charlie's, See The Difference!
As a family-owned business local to Herrin, Carterville, and Marion with nearly 40 years in business, we demand outstanding work ethic from our team and they proudly meet it every single day. Anytime you call us, we will deliver the same unparalleled service.
If you're a Herrin resident, give a company that has strong values and prizes a strong work ethic a try. Charlie's Air & Heating is like no one else; call (618) 985-2502 today and find out what we can make more comfortable for you.
for Herrin, IL
Our Reviews by City
Awesome service. Excellent customer service
Gualdoni - Herrin, IL
Great service as always trusted advice.
Sarah - Herrin, IL
Clen n Check
Hooks - Herrin, IL
Super good and fast
Vaughn - Herrin, IL
Lori - Herrin, IL
Very prompt, friendly service. Knowledgeable and takes the time to explain everything.
Samantha - Herrin, IL
Above and beyond excellent service
Tadda - Herrin, IL
Great job as usual.
Jennifer - Herrin, IL
Excelled the averaged
Bailey - Herrin, IL
Greg - Herrin, IL
Charlie’s very professional team
Ray - Herrin, IL
Boner - Herrin, IL
Pete was very informative about a new heating and air system. He has given me good options to choose from.
Sollami - Herrin, IL
Great job Justin review
Jacobs - Herrin, IL
Very friendly and courteous great job
Brad - Herrin, IL
Sylvia - Herrin, IL
A big thank you to Charlie’s for repairs to our air-conditioning unit that is very old and helping us to get some air while we contemplate buying a new system. Our technician Daniel was very personable and helped us and was very knowledgeable about our system and what we needed to do to get the best out of it thank you very much we will recommend Charlie’s.
McBride - Herrin, IL
Very good technician and service
Cramer - Herrin, IL
Sylvia - Herrin, IL
Charlie’s was able to give me Service within a few hours of my call! Daniel the service rep was very personable and professional. He explained what was going on and what it would take to fix the problem. I am very satisfied with the repairs.
Protsman - Herrin, IL
He did real good!
Arrived within a short time and diagnosed the problem quickly
Griffith - Herrin, IL
Polite, efficient, knowledgeable…Great
Rick Basler - Herrin, IL
Good experience…as always
Miskowsky - Herrin, IL
excellent service. very knowable. thanks
Kleckner - Herrin, IL
Fast friendly service at a reasonable price
Nochta - Herrin, IL
Very informative and helpful
PCSA 2022 Heating Check Up 2 Systems Prepaid. Both systems are operating efficiently at this time. Coils are clean, filters are changed as needed, and temperature rise is acceptable. Outdoor system for front office had a contractor showing signs that it was about to go bad. Replaced and verified operation of system.
PCSA 2022 heating check up renewal 2 systems Gas furnace and heat pump both check good. Replaced filters. Rises look good.
Quote for new heat pump install
Building had two systems down. One system was 5lbs low on 410A, charged system and verified operation. Performed leak search and found that high pressure switch on outdoor condenser unit is leaking. Needs to be replaced. Second system is completely empty (8lbs) of 410a. Performed leak search and found leak on indoor system’s bolt on TXV. TXV needs to be replaced. System is off at this time.
Inspect dryer vent. Poked some relief point to let water out. Taped over spots I poked. Strapped up flex pipe to joist. Suggested running the dryer dry a few times to dry the flex pipe out. Appliance guy suggested replacing white flex as it is a fire hazard. I would trust him on that and eventually look at replacement
Quote for 3 ton air conditioner and 95% gas furnace installation
Cleaned off vines off both units and washed, serious landscaping needs done. Replaced aluminum coil, pulled vacuum and charged by superheat, orifice.
Water Issue 7/28/22 Steve hooked up to unit using app, lowered blower speed, set blower profile to D, it adjusts speeds to help dehumidification. That should help with humidity. Water is pulling off coil due to dirty filter, he ordered a new one but if we have one in stock I’ll run one over. Replaced filter, were going to wait and see for a month before we complete call 8/31/22 closed call
Need to order evaporator coil. Model and serial updated in equipment history
Moved air handler for remodel. Added return duct in living room
AC not cooling well. Added 1lb of R22 to system and verified operation. System is starting to show age, causing it run less efficiently. Charge is acceptable at this time and temperature drop isn’t acceptable at this time.
AC Check Up - System Was not running to its full potential due to a bad dual capacitor and being 1 pound low on R22 refrigerant. Replaced capacitor and added 1 lb of R22, verified operation of system. System is now running much better and more efficiently, however, age, wear and tear of system is causing it to not run to full potential. Condenser coil is clean, but has big corrosion spot on bottom corner of it leaving piping exposed. Temp drop is acceptable at this time and house came down two degrees while I was here, which is a good sign. System running normally at this time.
Fan motor replaced. Unit cooling at this time
Possibly changing thermostat. Replaced t-stat
Replaced condenser motor & blade
Replaced fuse and corrected wire in t-stat. Paying 89.00 for previous cll
PTAC unit making noise. Unit could use a cleaning. Filters very clean. No furniture no carpet, easy to hear compressor rumble. Music studio.
Repaired copper liquid line. Pulled vacuum, charged with R-421A
Customers filter was too weak and got ripped, replaced with sturdier filter to avoided being sucked into system. System operation is normal at this time
Start PCSA 2022 a/c check up. System is running efficiently this time, drain is flushed and clean, filter is changed and provided by customer. Blower capacitor was weak, replaced with new and verified operation. Outdoor coil is mildly dirt, however, customer does not have a way to run hose to condenser coil. He is aware it cannot be hosed off at this time. Refrigerant charge is good and temperature drop is acceptable.
Return to replace control board, clean blower, and start PCSA per Quote $815.00 .Replaced board and completed spring ck.
Complaint not reaching set point won't shut off Only charged for filter which was a plugged MPG from Pass. Replaced with regular 1” 20x20 and junked mpg. Charge looks good. Unit fully operational. Witnessed a groundhog crawl under house as I pulled in the driveway. Told customer if filter doesn’t work we may need to do a duct inspection. If we are to come back and do an inspection groundhog must be removed and crawl space must be sealed. House also has an addition with vents installed into the trim. Not 100% sure if unit is even properly sized. Diag waived as we were just out here.
PCSA 2022 RENEWAL -AC Check Up. Completed Spring Pm unit in good order
PCSA 2022 a/c check up prepaid Everything was clean and checked out well. System is operating normally at this time.