Energy IL AC and Heating Experts
Charlie’s Air Conditioning & Heating has been warming and cooling Southern, IL homes and businesses for almost 40 years. We’ve been serving Energy, IL and the surrounding areas since 1982.
Read our fantastic reviews and find out why your Southern, IL neighbors consider us to be their nearby heating and air company in Energy, IL.
for Energy, IL
Our Reviews by City
Mason - Energy, IL
Great service! Steve was very thorough & explained all that he checked.
Storey - Energy, IL
I give u guys A for good service
He does a great job.
Melvin - Energy, IL
John - Energy, IL
Very nice young man very professional and polite.
Quote for 95% Furnace and 16 SEER York air conditioning unit
All systems check good in cooling still need a 24x24x2 for system #4 win air was out when I checked. All filter sizes recorded in folder
Added 2 lbs of gas unit was low. Did not put any refrigerant last year. Would like to come back out in May or June and just put my gauges on to follow up and monitor
Customer has part in needs installed and ice machine cleaned . Cleaned ice machine installed part. All material provided by customer.
Condenser Coil Cleaning, AC Maintenance & 20x25x5 Filter Change ....As Per Quote
PCSA 2020 Heating Check Up Checked electric heat, inspected all electrical, checked filter, tested heat pump, checked charge, tested defrost system is heating
PCSA 2020 Heating Equipment Maintenance RENEWAL PCSA 2021 Cooling Equipment Maintenance Included Filters are changed by customer
2020 Fall PCSA Renew Customer would like 4 filters every spring check up. Everything was clean and operating normally at this time.
PCSA 2020 Heating Check Up ckd system cleared codes on board. New filter
Everything was clean and checked out well.
2020 Furnace Maintenance, 4th Quarter 20x25x5 Filter change and Condenser coil cleaning.
No Heat Phil replaced blower motor last December Repaired burnt wires from contactor, cycled heat Pat will call Monday to figure out payment
3 rd Quarterly Filter Change and wash cond. coil
Found out of tolerance single run capacitor replaced it all checks good. Filters changed by customer. Filter size listed incorrectly actual size is 20x25x1 will add an office alert for it.
Bad air flow to back room. Replaced flexible duct work in attic damaged by animals