Du Quoin IL AC and Heating Experts
Charlie’s Air Conditioning & Heating has delivered Du Quoin, IL excellent service for almost 40 years. We specialize in heating and air conditioning services as well as blown-in insulation.
Check out our glowing reviews and discover why your neighbors consider us to be their nearby heating and air company in Du Quoin, IL.
for Du Quoin, IL
Our Reviews by City
Diebolt - Du Quoin, IL
GREAT SERVICE AS ALWAYS
Best customer service!
Mifflin - Du Quoin, IL
Charlie’s Heating and Air have the best customer service and technicians, hands down! Daniel and Phil are knowledgeable, kind and take time to answer any questions. Charlie’s is always on time and if they are running behind, they will inform you by text message when they are on the way. We will ALWAYS recommend Charlie’s!! Very thankful for them and their work ethic!
PCSA 2021 AC Check Up Renewal completed pm on 4 A/c units. All ck. Ok, changed filters as needed provided by customer
PCSA 2020 Heating Check Up Renew Little over on charge. 475 on a 36 degree day with a discharge temp of 167 reduced to 425 psi and 143 degree discharge. All checks good. Changed filter
2020 PCSA Prepaid Check Up. Need parts for both humidifiers will quote.replaced parts
PCSA 4 Systems 2020 AC Check Up Renew & Done 5/13/20 2020 Heating Check Up Prepaid & Scheduled 10/13/20 Left furnace in church cannot get pressure switch tthe close by natural means. Need to come back. Trane m# tux100c948d1. S# 251snmk7g
Ckd system all in good order, cut drain and flushed very long run.
PCSA Spring 2020 AC Check Up Fall 2020 Heating Check Up Included Blower capacitor and capacitor on outdoor coil needed replaced. Everything else was clean and checked out well.
Quote for 2 1/2 ton 16 SEER York Heat Pump
Fan motor making a racket and not blowing very much air. Unit very low on charge. Needs est. ASAP.
8/7/2020 Indoor coil has a huge leak and needs to be replaced ASAP. 8/11/2020 Replaced indoor coil. System is operating normally at this time. Cleaned outdoor coil.
No AC fan running but not cooling .replaced contactor .