Makanda IL AC and Heating Experts
Providing air conditioning and heating to the residents of Makanda, IL and the surrounding areas since 1982, Charlie’s Air Conditioning & Heating is the top choice in Southern Illinois!
Check out our 5-star reviews to see why your neighbors consider us to be their nearby heating and air company in Makanda, IL.
for Makanda, IL
Our Reviews by City
Sam - Makanda, IL
Kyle provided excellent service in scheduling the appointment. Shawn was professional and did superior work. Charlie was great. I highly recommend this place.
Great service/Great price.
Phillips Jan - Makanda, IL
Daniel is very professional and friendly.
BBGOLFCARTS - Makanda, IL
Thorough & professional
Katie - Makanda, IL
Shawn was great—explained everything well, answered questions thoroughly, very professional & knowledgeable
Checked over system found unit low on r22, added one pound of r22 system is cooling
Charge Motor Home AC Units
NO heat, found orifice clogged, cleaned out, replaced broken thermostat, need to come back to replace with gas furnace thermostat
No heat code 3 and code 6. Cleared code, vacuumed all drains, pressure tubes and gutters. Cleared codes, cycled furnace. Furnace is in an unconditioned room, drain could also be freezing up on cold nights. Adjusted drain line in a few spots so it had a good even pitch, ran furnace for 40 mins had great water flow to outside. Increased furnace intake air volume, everything working great at this time
Faults showing vent issues cleaned gutters and recommend running it low temp at night to prevent ice build up
Replace Ventor Motor , Labor only , Part was out of warranty , Charlie got it covered for her . $130.00 To Replace under warranty
2020 Fall PCSA Renew 2021 Spring PCSA Included Filters changed by customers all checks good on both systems
PCSA PREPAID 2020 Heating Equipment Maintenance Electric heat does not engage on emergency heat. Only engages on temp differential. Customer has been made aware. Could not force defrost. Goodmanâ€™s will not jump in and out of cycle if the temp isnâ€™t cold enough. told them to monitor it. Customer to be billed for filter
2020 PCSA 2 system check up heating visit prepaid
2020 Fall PCSA Renew Inducer motor is making a little noise. Customer would like a price to have it replaced being so close to warranty. Everything else is operating normally.
2020 PCSA Heating Check Up 2 Systems checked heat pump and electric heat on both systems, upstairs Ruud has a capacitor close to lower threshold, daughter is saving to replace upstairs system. Downstairs system checks out good
2020 Sumer pcsa changed both filters, flushed drains, inspected electrical, cleaned air handlers, cleaned condensers, checked charge, replaced capacitor on 5 ton unit system is cooling I sent him the bill through email Call to schedule winter visit, January should be good