Elkville IL AC and Heating Experts
Charlie’s Air Conditioning & Heating has been warming and cooling Southern, IL homes and businesses for almost 40 years. We’ve been serving Elkville, IL and the surrounding areas since 1982.
Read our fantastic reviews and find out why your Southern, IL neighbors consider us to be their nearby heating and air company in Elkville, IL.
for Elkville, IL
Our Reviews by City
Great service didn’t expect anyone to come out today
Jason - Elkville, IL 62932
Great Service As Usual
Pierce - Elkville, IL 62932
My technician arrived on time and did a through inspection. I had a few questions about programming my thermostat and he was very patient with me and answered all of my questions. I would whole heartedly recommend Charlie’s Air Conditioning and Heating. Great service and very reasonable prices.
Spiller-Pace - Elkville, IL 62932
Spiller-Pace - Elkville, IL 62932
Steve was on time, informative, thorough and very professional
Great Price, Awesome Service!!!
Linda - Elkville, IL 62932
Would like to be in a commercial for you and share my experience!!
Cinilou - Elkville, IL 62932
Technician was on time, very knowledgeable, safety conscious including precautions for COVID. He was willing to answer questions and very neat in completing his work.
PCSA 2022 Heating Check Up Renewal All checks good on both heat pump and gas furnace.
Inspection Furnace looks good. Blower, burners, pilot sensor, all check good. Confirmed operation of condensate pump. CO test came back safe. AC is very low on 410A refrigerant. Customer will look at doing a leak search in the spring. Just charged labor. No parts replaced at this time. Locked up and left thermostat in “off” position
PCSA 2022 Heating Check Up Prepaid All checks are good left a filter behind for customer change deeper into heating season. Unit heating at this time
Complaint: No heat, blowing cold air System operating properly at time of service
Cause of the issue was dead mice caught in the blower wheel. Removed blower wheel and cleaned it. Blower motor still has a lot of vibration to it. When it does fail, recommend replacing wheel and motor both. Had to replace blower capacitor. Also cleaned secondary heat exchanger as much as possible. System is operating normally at this time.
Complaint no a/c blowing warm air Replaced bad dual run capacitor and checked charge. Unit cooling at this time
PCSA 2022 a/c check up prepaid Customer will swing by the shop and pay for and pick up a new filter 20x25x5 All checks are good
pcsa 2022, ac check up. System checks out good, filter is changed and outdoor coil is clean.
Complaint no a/c Bad single run capacitor has been replaced unit cooling at this time
Found bad dual cap. System cooling at this time
2021 PCSA furnace maintenance prepaid Replaced wonky thermostat. All checks on furnace are good. Filter clean
Cleaned HP with customers permission and disconnected hose from faucet to let drain All checks are good on dual fuel system
PCSA 2021 heating maintenance free w/ install All electric heat coming on cust,er provided filter left Over from install all checks in air conditioning mode good 20 degree drop Updated filter size
Gave quote to insta dual fuel system
Gave quote for new AC unit and air handler
Replaced indoor TXV 1 yr parts & labor
PCSA 2021 PREPAID AC CHECK UP Subcooling seemed a bit unreasonable at 22 degrees Unit says target of 10 from manufacturer Took a littl gas out for a total of 14 degrees subcooling All other checks good filter is clean
PCSA 2021 PREPAID AC CHECK UP
Complaint AC Freezing Up System low on freon added 2# R-22
PCSA 2021 AC Check Up Free w/ Install
Complaint unit making noise . No issues found replaced filter customer stock.
Customer Complaint is the thermostat showing its 77 but cold in house sometimes. Found supply air vent blowing warm air on thermostat causing system to short cycle. Set chair over vent and returned to see if problem was any better. Customer purchased service agreement
Water in inducer needs flue tee. Ck warrantyâ€™s.
Rewired elec. furnace. All 3 heaters work. A/c working. Please bill customer.