Royalton IL AC and Heating Experts
Charlie’s Air Conditioning & Heating has delivered Royalton, IL excellent service for almost 40 years. We specialize in heating and air conditioning services as well as blown-in insulation.
Check out our glowing reviews and discover why your neighbors consider us to be their nearby heating and air company in Royalton, IL.
for Royalton, IL
Our Reviews by City
Battaglia - Royalton, IL 62983
Great Friendly Service
Lynch - Royalton, IL 62983
Hoffner - Royalton, IL 62983
Great company! Excellent service and very respectful. I would recommend this company to everyone. Thanks so much for the quick response l
Mike - Royalton, IL 62983
Shawn was very helpful and thorough. He was able to answer all my questions.
Expensive for a 12 dollar capacitor
Shawn - Royalton, IL 62983
Phil is a great guy
Brenda - Royalton, IL 62983
Very professional and very respectful. Shawn done a fantastic job. This will be our place to call from now on. Thanks so much for getting here quick
Sean is a wonderful young man if I need anything else I want him to come out does an awesome job
Lighthouse - Royalton, IL 62983
Great guy already need a parent's very professional he's got a good man there
Battaglia - Royalton, IL 62983
Very thorough and courteous
Great Experience !
Mike Hooker - Royalton, IL 62983
My experience with Charlie's was seamless. They took care of everything. They gave me a great price and an excellent warranty and set up my financing for me with just a few questions over the phone. Their install team was fast and friendly and had me going in no time at all !
PCSA 2022 Heating Check Up 2 Systems Prepaid. Both heat pumps are running efficiently at this time, auxiliary heat kicks on as needed, filters re changed and defrost is working properly.
Found that system is running an electric key, but due to age of system it is not keeping up as it should. However heat kit is heating functionally at this time.
PCSA 2022 Heating Check Up Renewal. Downstairs system is heating efficiently at this time, had a capacitor going week, replaced and verified operation of system. Downstairs system however was completely out of 410A. Conducted a leak search and found that there is a leak on the reversing valve. Customer would like to wait till January for quote, it is running in electric heat until then.
All checks good on new heat pump. Filter was clean. Left it for now. She has an extra from the install still.
Start PCSA 2 System Heating Maintenance. Both gas furnace and heat pump are eating efficiently at this time, all filters are changed, and temp are acceptable.
PCSA 2022 Heating Maintenance. All systems check out good and are ready for winter.
Crossover 12 inch flex was down, rehung but it’s heavily water logged. This will help but it needs to replaced. Customers want it replaced, will get materials and schedule it up. 11-30-22 Replaced flex and strapped up tightly.
2022 Fall Check Up PCSA New 10/11/22 Complaint no heat nothing coming on. Cause of the issue is gas has been turned off to the location until a repair on the outdoor grill supply line has been made. Customer will have the line repaired and then call us to come out and do heat check up. Cleaned outdoor coil in the meantime to help AC run more efficiently (1/2 labor) Indoor coil may need cleaned in the future. 10/31/22 Returned to perform heat check up. Inducer motor bearings are making a little noise and main limit has some water damage. If parts are under warranty, would recommend replacement. If not, customer will monitor for any changes in system operation. Everything else was clean and checked out well.
Believe heat kit is under sized. 10 kw on 1568 square feet.
Complaint: No Heat - Short Cycling Blew bug out of pressure switch hose. Furnace fired twice in a row before leaving. Watched diaphragm make a little slow on switch, wiggled it a little with small screw driver to make sure it wasn’t caught. Seems to be performing well. Unit heating at this time
Complaint unit in barn kicking on and off. System refrigerant was tripping out on high pressure. Took 1lb of 410A out of system and verified operation. Checked charge and superheat. Need to continue to monitor system. System is working at this time.
AC not cooling. Found that system had a bad capacitor, replaced and verified operation. Since this was second issue in a month I signed customer up for PCSA plan. Proceeded to do check up on system and ,ale sure we don’t have anymore issues. Filter is routinely changed by customer, coil is clean and temperature is coming down in house. System is running efficiently at this time. Thermostat resets itself randomly, might be malfunctioning. Customer is going to monitor
Complaint no cool . Replaced capacitor for compressor
Complaint water leaking on the floor Slower blower speed, checked low side pressure, cleaned coil, vacuumed drain. Need to confirm whether drain is trapped under house. If homeowner removes a section of skirting for access I will verify drain is code at no charge, if trap needs to be added time and materials will be charged upon completion. Gaping hole where drain and line set run through house is most likely pulling hot air into return. Should be sealed with spray foam
Gave quote for new AC system
PCSA 2022 a/c check up free w/ install
It in easy seal ,topped off charge.
PCSA 2022 a/c check up prepaid 2 system. Both systems check out good and I really efficient at this time, filters are changed by customer, drains are flushed, and outdoor condenser coils are clean. Capacitor on downstairs system is going bad, customer is aware and wants to wait till next year check up to change it out.
Added 2 pounds of R 22 to system, highly recommend a leak search unless customer would like a new system. She is considering having a new system put in.
Cause of the issue was system was 1 lb low on R-22 which was causing the coil to freeze. System appears to be operating normally at this time.
No AC - Not blowing air . 1 vent off in crawl.
Bad relay return ASAP to replace, hot wired motor. Quoted 215.00 for relay R-22 .?
PCSA 2022 RENEWAL - AC Check Up - And Do Mitsubishi
AC not cooling well. 78 in house, stat set at 72. Condenser fan motor replaced