Royalton IL AC and Heating Experts
Charlie’s Air Conditioning & Heating has delivered Royalton, IL excellent service for almost 40 years. We specialize in heating and air conditioning services as well as blown-in insulation.
Check out our glowing reviews and discover why your neighbors consider us to be their nearby heating and air company in Royalton, IL.
for Royalton, IL
Our Reviews by City
Great Experience !
Mike Hooker - Royalton, IL
My experience with Charlie's was seamless. They took care of everything. They gave me a great price and an excellent warranty and set up my financing for me with just a few questions over the phone. Their install team was fast and friendly and had me going in no time at all !
PCSA 2021 AC Check Up 2 system prepaid Downstairs system needed 8 lbs of R-410A. Customer wants leak search when possible. Downstairs system also has a fault in electric heater package. Half of the 3rd heat strip is drawing amperage at all times. Customer may want to replace next winter. Upstairs system will need new condensate pump during AC check up next year. Everything is operating normally. 4/12 Performed leak search. Found leak in liquid line service valve. Was able to work with valve and stop leak at this time. Future use of service valve may require replacement in the future. Everything else appears to be operating normally.
2021 PCSA a/c 2 system check up renewal Everything was clean and checked out well. Systems are operating normally at this time.
Free With Install AC Check Up Puron levels were a little off. Corrected levels and system is operating normally. Recommend double checking Puron levels during Fall Check up. Everything else was clean and checked out well. System is operating normally at this time. 2021 AC Check Up Free W. New Install & Done 4/8/21 2021 Heating Check Up Free W. New Install 2022 AC Check Up Renewal
No heat found board was putting out call for ac and heat. Disconnected the ac, furnace working. Ordered new board, signed up on service agreement. Set up appointment for Monday at 8 am. Need to bring a 2 inch pvc coupler Replaced board, cleaned furnace, installed nest thermostat, need to come out and replace 2 inch coupler on drain when itâ€™s not raining
Cleaned boiler, checked safeties, inspected flue vent. Part of it is rotting out, will address it this summer. Signed up on service agreement
Estimate For 95% Gas Furnace and AC unit
Estimate for new york furnace
2020 Heating Check Up Prepaid Replaced upstairs outdoor coil fan motor and blade (parts warranty). Everything else was clean and checked out well.
Unit frosting up Outdoor temp not sufficient for diag in cooling mode. Runs great in Heating we will check back next spring
Complaint: No Heat. Sticker psi. Swt.
2020 Heating Check Up Renew & Scheduled 9/28/20 2021 AC Check Up Included
Ckd unit all in good order.
Estimate for York package unit