Royalton IL AC and Heating Experts
Charlie’s Air Conditioning & Heating has delivered Royalton, IL excellent service for almost 40 years. We specialize in heating and air conditioning services as well as blown-in insulation.
Check out our glowing reviews and discover why your neighbors consider us to be their nearby heating and air company in Royalton, IL.
for Royalton, IL
Our Reviews by City
Hoffner - Royalton, IL 62983
Justin done a fantastic job. Very professional and courteous.
Kirkpatrick - Royalton, IL 62983
Battaglia - Royalton, IL 62983
Great Friendly Service
Lynch - Royalton, IL 62983
Hoffner - Royalton, IL 62983
Great company! Excellent service and very respectful. I would recommend this company to everyone. Thanks so much for the quick response l
Mike - Royalton, IL 62983
Shawn was very helpful and thorough. He was able to answer all my questions.
Expensive for a 12 dollar capacitor
Shawn - Royalton, IL 62983
Phil is a great guy
Brenda - Royalton, IL 62983
Very professional and very respectful. Shawn done a fantastic job. This will be our place to call from now on. Thanks so much for getting here quick
Sean is a wonderful young man if I need anything else I want him to come out does an awesome job
Lighthouse - Royalton, IL 62983
Great guy already need a parent's very professional he's got a good man there
Battaglia - Royalton, IL 62983
Very thorough and courteous
Great Experience !
Mike Hooker - Royalton, IL 62983
My experience with Charlie's was seamless. They took care of everything. They gave me a great price and an excellent warranty and set up my financing for me with just a few questions over the phone. Their install team was fast and friendly and had me going in no time at all !
HVAC Repair Heating Maintenance PCSA 2023 Heating Check Up Prepaid Completed heating maintenance, cleaned filter and flame sensor, vacuumed drain, checked system operation and found no issues, looked for gas leaks and found none, made sure system is working properly System is heating at this time
Furnace Service Heating Maintenance PCSA 2023 Heating Check Up 2 Systems Prepaid Completed heating maintenance, coils are clean, replaced upstairs filter, downstairs filter is clean, checked system operation and found no issues, made sure both systems are working properly Both systems are heating at this time
2023 PCSA Heating Check Up Renewal Heating Service HVAC Service Agreement All operations checks good
Estimate to replace unit
2023 PCSA Heating Only Check Up Renewal Heating Maintenance. System is heating efficiently at this time, temperature rise is great, and filter is changed routinely by customer.
2023 PCSA Heating Check Up Prepaid Heating maintenance Operations checks all good on geothermal. Checked charge, water pressure, line temps, air temps, water temp, capacitor, and filter. Recommend Paul gets filter replaced. He is going to take care of it.
Quote for het pump replacement
AC Maintenance PCSA 2023 AC Check Up Prepaid 2 Systems. System is cooling efficiently at this time, outdoor coil is clean, filters changed by customer routinely. Outdoor unit’s contactor was showing voltage drop so I replaced it under warranty. Everything else checks out great. Customer declined personal home’s system maintenance at this time because they are having it replaced.
System is completely frozen over all the way to the compressor, we need to let it thaw before I can make an accurate diagnosis. I have fan set to “on” for the time being. We will get back out here ASAP. 8-4-2023: Returned and all ice was melted from system, found that cause was the filter being dirty and restricting airflow. Condenser coil was also extremely dirty and restricting airflow. Since we had two Issues that could’ve been prevented on a maintenance, customer agreed to a PCSA plan. I performed a full inspection on the system and found that indoor blower had a capacitor that was extremely weak. Replaced capacitor so motor could run at its full potential. We will continue to monitor system on future maintenances. At this time, everything checks out good and system is cooling efficiently.
AC Maintenance PCSA 2023 AC Check Up Prepaid Both units look good cleaned coils checked charged flushed drains.
Top Off Freon - Doing Install This Fall NC Topped off unit, customer replaced filter, system is cooling at this time
2023 Spring Check Up PCSA Renew Discoloration on coil was mainly dirt and debris. Sprayed coil with cleaner and evap fresh to help remove some of the smell and dirt buildup. Wasn’t able to clean outdoor coil. Customer will be repairing outdoor water faucet and cleaning outdoor coil when possible. Everything else was clean and checked out well. System is operating normally at this time.
Dirty condenser causing hps trip unit was short cycling. Sprayed with hose quickly. Cooling at this time. 375 head
Added R22 and verified operation of system, leak is pretty bad and compressor has been running without refrigerant which is causing a lot of stress on system. There is no guarantee that system will cool home efficiently will hold charge, customer is aware of this . Pete is coming out for an estimate next week.
Complaint: No AC- Blowing warm air Bad dual run capacitor, replaced, cooling at this time
Noticed several potential issues when servicing system. Coil temperature is hovering close to freezing. Cause of the issue is a weak blower motor which also has damaged bearings that are causing the blower wheel to occasionally make contact with the housing. Also noticed the primary drain pan has rotted through which is causing the door on the air handler to also rust through. Secondary drain pan has been collecting water but also has accumulated a lot of rust. Disconnect on outdoor coil died during appointment and had to be replaced for ac to work. System appears to be operational at this time. Strongly recommend system replacement if possible.
Geothermal system is cooling efficiently at this time, water pressures are good, temp drop is great, refrigerant pressures and temps are acceptable, and filters are changed routinely by customer. Blower wheel seems like it is starting to spin a little off balance, and capacitor is starting to weaken but is within range. Will monitor both until next check up. Customer also has filters in ceiling vents and a 5” at the system. I advised to leave the one at the system and remove the ones on the ceiling.
2023 PCSA Ac Maintenance ✔️
Air Conditioning Maintenance PCSA 2023 AC Check Up Free w/ Install. System checks out great, coil is clean, filter is clean and temp drop Is great.
AC Maintenance PCSA 2023 AC Check Up Prepaid. System is cooling at this time, filters are changed, drain was mildly clogged so I flushed thoroughly. Outdoor coil is clean and I scrubbed away the moss that was covering the outdoor system.
AC Maintenance PCSA 2023 AC Check Up Renewal. Both systems check out good at this time, filters are changed and I thoroughly cleaned outdoor systems. Temp drop is great and drains are clean.
Heat Pump Repair Return and replace reversing valve Conducted a leak search. No luck on isolating exact leak location, it does seem as though the leak is in the outdoor unit. Service valves are locked down and common port pressure continued to drop. Valves are still locked down, thermostat is set to emergency heat, disconnect is off, outdoor fan is disconnected for ease of leak search next trip out. We may have to dump the nitrogen and put some more 410A in and go back in with a detector to start. We will call to schedule 2/6/23 Steve returned, added 410a to nitrogen and leak searched outdoor unit, confirmed with detector and bubbles that the suction line accumulator is leaking underneath. Bubbled and leak detected rest of outdoor unit, all coil ends and copper connections, found no other leaks. Need to get an accumulator