Cambria IL AC and Heating Experts
Charlie’s Air Conditioning & Heating has been warming and cooling Southern, IL homes and businesses for almost 40 years. We’ve been serving Cambria, IL and the surrounding areas since 1982.
Read our fantastic reviews and find out why your Southern, IL neighbors consider us to be their nearby heating and air company in Cambria, IL.
for Cambria, IL
Our Reviews by City
Bastien - Cambria, IL
Great service, quick and efficient!
Wild - Cambria, IL
Justin arrived shortly after my call, was very friendly and very quick and efficient at his job. I am very impressed with the whole process and how quickly everything was taken care of for an emergency appointment on a Friday afternoon.
Silva - Cambria, IL
Very good customer service
Good service, nice guy.
Morgan - Cambria, IL
He was running approximately 45 minutes late. Although they did call and get me in on a cancellation a day early so for that I am grateful for a air conditioned sleep. My husband was the one who interacted with him for the most part but he said he was a nice guy and he did us a favor by giving us a free filter so overall great experience.
Mandy - Cambria, IL
Potter - Cambria, IL
Phil always does a great job and answers all of my questions.
Great information! Reasonable price.
Mandy - Cambria, IL
Potter - Cambria, IL
Great job of explaining everything, making recommendations and answering all of my questions.
AC check up
Rowatt - Cambria, IL
Great service. Good advice.
Pottorff - Cambria, IL
Was very pleased with tech. Attitude, knowledge, professionalism.
always excellent service
Potter - Cambria, IL
Put foam strips on filter door
Found that outdoor condenser unit had a weak capacitor and bad contactor. Replaced both capacitor and contactor with new and verified operation. System is running at this time. Signed customer up for service agreement.
Need to do leak search and connect vent to bathroom under house. Performed leak search and found a massive crack in a copper line inside indoor coil. Removed coil, sealed crack, and then reinstalled. Due to the age of the coil another leak maybe possible but customer will monitor and let us know of any changes in operation. Recharged system and did as much as possible to keep water from dripping from drain pan. Didnâ€™t see any cracks or leaks in the drain pan itself. Inspected duct under the house to see what materials would be needed to attach vent in bathroom. Informed customer of mold under the bathroom. After customer has dealt with the mold, we can attach bathroom vent. System is operating normally at this time.
PCSA 2022 a/c check up renewal System was 1.5 lbs low on R-410A. Everything else was clean and checked out well. System is operating normally at this time. Customer would like to schedule a leak search when possible and would also like the vent in his bathroom connected to the trunk line under the house.
2- 20x25x1. 6-16x25x1 flushed pumps & drains.
AC is low of freon. Topped off charge by superheat. Unit needs new lineset
PCSA 2022 RENEWAL - AC Check Up Condenser fan motor is starting to show signs of the bearings wearing out. Still seems to be fully operational but would recommend replacement during a future check up. Everything else was clean and checked out well. System is operating normally at this time.
Loose connections at contactor
Installed 3 ton 16 SEER York heat pump
Complaint no a/c Cause of the issue was bad high pressure switch. Replaced switched under parts warranty.
Cause of the issue was short in low voltage wiring going to outdoor coil. Replaced section of damaged wire. Short also damaged thermostat and wouldnâ€™t being on AC. Replaced thermostat. System was also 1 lb low on R-22 and had a very weak capacitor on outdoor coil. Replaced capacitor. System is operating normally at this time.
Gave price for replacement of 3 ton heat pump
Washed both systems. Contactor points pitted will wait due to units age. 30 yrs. old
2022 Spring Check Up PCSA New System was 2 lbs low on R-22. Customer wanted to start service plan. Everything else was clean and checked out well. System is operating normally at this time.
Complaint no a/c . Cleaned all condensers west side apt. #1-12
# 14 new filter vacuumed drain #19 new filter 3# R-410A all condensers in complex need washing.
Replaced condenser motor 10yr. Part 1 yr. labor
AC Not Cooling .Breaker tripped, swapped breaker from water heater, need electrician to ck wiring and panel. New capacitor,needs filter, and wash condenser. No outside hydrant.
PCSA 2022 a/c maintenance prepaid Everything was clean and checked out well. System is operating normally at this time.
PCSA 2022 a/c maintenance free w/ install. System checks out good
4/5/22 Kitchen unit indoor coil is covered in oil. Pressures donâ€™t seem too bad. Need to check charge on a hot day more attention is needed to rule out oil coming from a different source other than refrigerant lines Hallway/classroom unit seems low on charge. Found leaking schrader. Charge check needs done on hot day and possible leak search. -Shawn Both Sanctuary systems are operating normally at this time. Puron levels are within range and everything electrically checked out well. The only concern was freeze stat on south system at one point tripped but once temperatures both outside and in the Sanctuary went back up, it never tripped again. Will monitor during future check ups to make sure the freeze stat isnâ€™t malfunctioning. Everything else checked out well. -Daniel 4/11/22 Hallway system needed capacitor on outdoor fan motor and 2 lbs of R-410A. Puron levels on kitchen system looked normal at this time. Will monitor during future check ups.
Heat & AC Repair Contractor - PCSA 2022 a/c maintenance prepaid Package Unit had a very dirty filter and evap coil. Replaced filter and cleaned coil. System also needed new capacitor on condenser motor and compressor. Split system needed a new capacitor on condenser coil as well and 1 lb of R-22. Everything else was clean and checked out well. Both systems are operating normally at this time.
Smart Thermostat Installation - Showed both 3 and 4 how to use thermostats.
Heating Repair - Heat won't shut off. Found stuck on sequencer. Replaced sequencer