Carbondale IL AC and Heating Experts
Charlie’s Air Conditioning & Heating has delivered Carbondale, IL excellent service for almost 40 years. We specialize in heating and air conditioning services as well as blown-in insulation.
Check out our glowing reviews and discover why your neighbors consider us to be their nearby heating and air company in Carbondale, IL.
for Carbondale, IL
Our Reviews by City
Great inspection and estimate!
Weldin - Carbondale, IL 62901
Justin was very thorough, helpful, and transparent. Much appreciated, will use again!
Nancy - Carbondale, IL 62901
Gerson was so polite and extremely efficient. He answered all my questions and kept me informed at all times!
Pat - Carbondale, IL 62901
As usual Shawn did a fantastic job
Professional and Respectful Service
Jones - Carbondale, IL 62902
Gerson was respectful of our home and the service was professional.
Foland - Carbondale, IL 62901
He was nice and thorough. Changed the two filters after checking everything out
Great Service, Wonderful Worker
Anna - Carbondale, IL 62901
Daniel was fantastic when we needed AC repairs after hours during the heat. He was very friendly and explained what was happening with the unit. I always love working with Charlie’s due to the workers being so friendly and informative.
Matt - Carbondale, IL 62901
great service I am very glad I have Charlies
Yancey - Carbondale, IL 62902
have no problem
Paul - Carbondale, IL 62902
Daniel was early for the service appt which was great and he was very professional friendly and thorough. Thanks Daniel!
Talapatra - Carbondale, IL 62901
Excellent overall experience
Always dependable and excellent service
Parks - Carbondale, IL 62901
Daniel very nice service is five star
Williams - Carbondale, IL 62901
Nigra - Carbondale, IL 62901
Charlie's was great! Daniel was polite, professional, knowledgeable, and wonderful to work with. I would recommend Charlie's for your HVAC needs. I will be using them again!
Professional and personable!
Steph - Carbondale, IL 62901
Great service & friendly. Highly recommend!
Ronn - Carbondale, IL 62901
Shawn came by promptly at our agreed upon time and had my A/C back up and running within minutes! He was very handsome too I must say
Carlos - Carbondale, IL 62901
All of the crew from Charlie’s is so polite and respectful and deliver excellent service So glad we have them to help!
Danaher - Carbondale, IL 62901
Finger - Carbondale, IL 62901
Knapp - Carbondale, IL 62903
Dillard - Carbondale, IL 62901
Tibrewala - Carbondale, IL 62901
was very friendly and was explaining everything for the system
Great service!! Prompt response to my call!!
Sherry - Carbondale, IL 62901
Justin was my repair man. He was so very kind to explain every thing that he was doing. My problem was solved and he was on his way. I would highly recommend Charlie’s Heating and Air Conditioning to solve any of your problems!! They were amazing!!!
Having problems with our AC just before company arrived called Charlies htng.an AC they came out and serviced us immediately.very pleased with the res
Bryant - Carbondale, IL 62902
McKinley - Carbondale, IL 62901
Kolkmeyer - Carbondale, IL 62901
Harrison was very efficient and polite. Very pleased.
Inspection and system evaluation. Home inspector said the furnace would not stay on. This was due to gas pressure being set to high. I adjusted gas pressure and verified the system was no longer kicking off. 80% natural gas furnace is heating well and safely at this time, all electrical components check out good. Home does need a CO detector. Outdoor system takes R22 refrigerant, however, pressures are good at this time and is cooling the home efficiently. Gabe and I discussed the age of the system, refrigerant concerns and overall condition of system. I would highly recommend a maintenance plan if he chooses to go forward with home purchase due to the system’s age. Until then, system is heating and cooling normally.
2023 PCSA Pre Paid Heating check up, Heating Maintenance Completed heating maintenance, cleaned flame sensors, coils are clean, filters are in good condition, checked air temps, checked blower and inducer amps, checked gas pressures, checked igniter resistance, downstairs unit has a lot of humidity in certain rooms and this may be caused by some heat gain from outside Made sure both systems are working properly Both systems are heating at this time
Upon arrival compressor coil was very dirty, after cleaning condenser coil compressor was not starting, after installing hard start kit compressor started and found unit to be low on refrigerant so I added refrigerant until I got decent pressures System is cooling at this time
Heating Maintenance PCSA 2023 Heating Check Up 2 Systems Prepaid Completed heating maintenance, coils are clean, will need to order a filter for downstairs unit, flushed drains, checked air temps in electric heating mode, checked AC operation in cooling mode due to outdoor temperature being too hot to run heat pump in heating mode and found no issues, checked blower and electric heat amps, checked capacitors, made sure both systems are working properly Both systems are heating at this time
Completed heating maintenance, cleaned condenser coil, flushed drain, used extra filter from install to replace old one, checked air temps in electric heating mode, checked blower and electric heat amps, checked cooling operations since outdoor temperature is not cold enough to run heat pump, found no issues System is cooling at this time
Completed heating maintenance, coils are clean, replaced filter, checked air temps in heat pump and electric heating mode, checked blower and electric heat amps, checked compressor and outdoor fan amps, checked capacitor, capacitor is starting to go weak but is working properly at this time, made sure system is working properly System is heating at this time
Heating Maintenance PCSA 2023 Heating Check Up Prepaid Completed heating maintenance,replaced filters, cleaned flame sensors, vacuumed drains, left condensation drain was detached so I reconnected drain, checked air temps, checked blower and inducer amps, checked blower and inducer capacitors, left unit igniter resistance is over 100 ohms and may need replaced soon, made sure both systems are working properly Both systems are heating at this time
System is heating efficiently at this time, outdoor coil is clean and filter is clean. Temperature rise is good and electrical components check out good. Previously replaced parts are good as well.
Complaint unit not keeping up. Added 1lb of R22 and verified operation.
Heating Maintenance PCSA 2023 Heating Check Up Prepaid. System is heating efficiently at this time, auxiliary heat kicks on when needed, filter’s changed and provided by customer, outdoor coil is clean and I cleaned filter grille, changed batteries in thermostat, and temperature rise is great.
Heating Maintenance PCSA 2023 Heating Check Up Prepaid All operations checks good on gas furnace. Vacuumed hoses and drains, filter is clean, rise in low is 30 degrees. Cleaned flame sensor and checked electrical.
No AC. Found and replaced bad dual run capacitor. Cooling at this time. Filter is clean
Gave customer Approx, price for AC system install
Leak search. Reschedule to come back and add leak stop and charge with 421 and filter drier change. Did not replaced drier. Charged back up with 421A. Vacuum run on lineset. Used 4 lbs of 421. Added leak stop. Cooling at this time
Cleaned coil, vacuumed drain replaced all filters. Added 2 lbs of 410A all other checks good
AC Maintenance PCSA 2023 AC Check Up Renewal. System is cooling efficiently at this time, outdoor coil is clean and housing has been scrubbed with cleaner, and filter is clean. Tennant Said that there has been a stale smell coming from the vents. I recommended that they kept the blower on circulate to continue moving air, they also said they turn up the thermostat when they leave the house. I recommended that they find one number on the thermostat they are comfortable with and keep it at that so the air can be continuously conditioned even while they’re gone. This will most likely help with humidity and any problems with smell.
2023 PCSA A/C Maintenance. System is cooling very efficiently at this time, both filters are changed, outdoor coil has been cleaned, and refrigerant charge is holding after adding refrigerant on previous visit. Customer does not want to do a leak search at this time.
2023 PCSA A/C Maintenance. System is cooling at this time, filters changed routinely by customer, outdoor coil is clean, drain had mild buildup so I added pan treatment to system to help prevent any future clogs.
AC Maintenance 2023 AC Check Up Free w/ Install. Both systems are cooling efficiently at this time, outdoor coils are clean, and drains are flushed. Added thumb gum behind both thermostats and added foam tape to exposed copper on outdoor units per customer’s request. Filters are clean and drains are clear.
PCSA 2023 A/C maintenance. A/C check up. Completed cooling maintenance, cleaned coils, flushed drain, filter is provided by customer, checked air temps, checked blower amps, checked compressor and condenser fan amps, checked capacitor, made sure system is working properly System is cooling at this time
System was 2lbs low on R22. I explained to customer there is no guarantee on refrigerant and I charged system and verified cooling. I performed a quick leak search and immediately found a major leak on indoor coil. Gave a rough quote to customer for repairs and she wanted to add the refrigerant and wait on repairs until next summer. We will also get her a quote on a new system because that will most likely be a better option due to system’s age.