Carbondale IL AC and Heating Experts
Charlie’s Air Conditioning & Heating has delivered Carbondale, IL excellent service for almost 40 years. We specialize in heating and air conditioning services as well as blown-in insulation.
Check out our glowing reviews and discover why your neighbors consider us to be their nearby heating and air company in Carbondale, IL.
for Carbondale, IL
Our Reviews by City
Chris - Carbondale, IL
Steve was just a wonderful guy, full of life, and seemed to do great job on a unique project (though we're pressure testing that right now).
Carlos - Carbondale, IL
Daniel arrived on time, was very friendly, professional and did a great job explaining the work he did. He finished everything in just about an hour. Ac is running again. And price is very reasonable.
Pat - Carbondale, IL
Shawn was the best very effiecent and professional
Norrington - Carbondale, IL
You guys are the best. Phil knows the job and does the job! Thank you.
Awesome job & company
David - Carbondale, IL
Excellent all around!
Soeka - Carbondale, IL
Great Service, Very Friendly and Knowledgeable
Anna - Carbondale, IL
Shawn and Justin were both very knowledgeable, friendly, and provided excellent service. They answered all of my questions and made sure to show and explain things to me throughout the service visit that were very helpful. I highly recommend and will be utilizing their services again.
Courteous, prompt and professional
Rankin - Carbondale, IL
Was on time. Checked furnace. Answered questions.
Knapp - Carbondale, IL
Insightful guidance for new updates
Lori - Carbondale, IL
What reasons my YORK 2001 HVAC Heat Exchanger failed were things I could explore with online U tube videos after working with this specialist contractor’s customer service and dedication to repair issues of HVAC YORK equipment. Thank you for great service to the caring homeowner.
always very nice
Yancey - Carbondale, IL
Paul - Carbondale, IL
He was on time and left things working and clean.
Stephanie - Carbondale, IL
Shawn ALWAYS does an incredible job!
Paul - Carbondale, IL
Phil was excellent. On time precessional left no mess and gave a thorough explanation of what was going on.
Talapatra - Carbondale, IL
Kline - Carbondale, IL
I appreciate that Shawn called to notify me he was running late.
Bea - Carbondale, IL
Steve did a very good job,and the price was great too.
Good to know our system is in good working order.
Greer - Carbondale, IL
Dellingner - Carbondale, IL
Good Service, Friendly People
Simpson - Carbondale, IL
Each time I’ve used Charlie’s they were on time every time, did dependable work at a reasonable cost with friendly technicians.
Bill - Carbondale, IL
Shawn was competent and friendly
Cremeens - Carbondale, IL
McKinley - Carbondale, IL
McKinley - Carbondale, IL
Phil gave dependable and knowledgeable service, as usual.
Yancey - Carbondale, IL
Quoted install of 3 ton AC unit and coil
Found a loose wire nut going to fan motor. Tightened wire nut. Tested system start up over 10 times. Customer will let us know of any changes in operation. 5/23/22 Replaced defrost board again. Previous one was bad out of the box. System is operating normally at this time.
Replaced condensate pump, tested operation unit is operating correctly
Complaint no a/c System was completely out of Freon upon arrival with a lot of oil around the base of the outdoor coil. Customer would like a price on a new system.
Removed section of damaged wire and reattached disconnected wire from contactor. System is operating normally at this time.
AC Not Cooling Replaced dual run capacitor
Compressor won't come on . Wants to try hard start kit. Minor electrical adjustment
No refrigerant 5/13/22 Found and repaired leaks inside condenser coil. Pressurized system with nitrogen until we can return and refill it with the right Freon. Cause of breaker tripping was capacitor was wired incorrectly to compressor. Fixed wiring.
Quoted price for replacement of furnace and AC unit
REplaced condenser motor OEM part.
AC Not Cooling, unit frozen up. Thawed unit, added 3 lbs r 22, unit is cooling
AC Not Cooling Drain line was completely clogged and secondary drain line was completely detached. Cleaned indoor coil, both drain pans, and drain lines. Also replaced filter. System is operating normally at this time.
AC Won't shut off Cause of issue were bad Indoor and outdoor capacitors. The sequencer in Indoor Unit had caught on fire once and left a heater stuck on. Replaced sequencer and burnt wires. Replaced filter. System is operating normally at this time.
Complaint no a/c . Topped off charge by superheat 20 deg. Didnâ€™t have access to inspect A/ coil or filter.
Complaint no a/c Cause of the issue was a bad capacitor on outdoor coil. Replaced capacitor. Blower motor was also making a lot of noise and not moving much air. Blower wheel had to be centered and cleaned. System is operating normally at this time. Customer maybe interested signing up for a service plan in the near future to help clean and maintain the system.
PCSA PREPAID AC CHECK UP Reset defrost board outside and system started operating normally. System started and shut down multiple times as needed. Possible cause of the issue is the defrost board. Customer will monitor and let us know of any changes in operation. Everything else was clean and checked out well. System is operating normally at this time.
Complaint: AC not cooling Unit completely out of gas. Bout a thousand dollars in refrigerant alone. Tenant is going to talk to landlord to see about splitting cost of possible repair. Tenant is aware that if the coil is the issue the cost may be around or upwards of $2000. I threw out leak stop as an option as well but noted it can be kind of a dice roll to use. Unit not cooling at this time diag collected
Repiped new heat exchanger for pool condenser. Moved thermistor to new exchanger, pressure tested and evacuated system, adjusted charge, system is operating correctly
175/280 S.L. 68 L.L. 84 Temp drop 15 degrees. Had to adjust Puron levels and fix a loose wire. System is operating normally at this time.
Start 2 system pcsa a/c maintenance Filters need to be ordered and replaced. Upstairs system appears to be slightly over charged but wouldnâ€™t take any Puron out unless it is necessary. Capacitor on upstairs heat pump is within range but will probably need replaced in the near future. Everything else was clean and checked out well. Both systems are operating normally at this time.
Apartment D had a bad reversing valve on outdoor coil. Tried to repair valve but was unsuccessful. Will order and replace valve as soon as possible.2 1/2 hr. Phil 5/6/22 Returned and replaced reversing valve. System needed at least 10 lbs of R-410A. Will need to double check Puron levels on a warmer day. System is operating normally at this time.
PCSA 2022 RENEWAL - AC Check Up All checks good cleaned unit and flushed drain Filter provided
PCSA 2022 a/c check up renewal System was 1 lb low on R-22. Everything else was clean and checked out well. System is operating normally at this time.
PCSA 2022 RENEWAL - AC Check Up. Both systems checked out good. Outdoor condenser units are clean.